This practice covers procedures for making and curing cylinder and beam specimens from representative samples of fresh concrete for a construction project. C 31/C 31M Practice for Making and Curing Concrete Test 1 This test method is under the jurisdiction of ASTM Committee C09 on. Concrete. ASTM Standards: 2. C 31/C 31M Practice for Making and Curing Concrete Test. Specimens in the Field. C 42/C 42M Test Method for Obtaining and Testing .
|Published (Last):||16 February 2018|
|PDF File Size:||20.60 Mb|
|ePub File Size:||20.44 Mb|
|Price:||Free* [*Free Regsitration Required]|
ASTM C31 – Making & Curing Concrete Specimens in the Field
It is very important for the integrity of any test to have clean, working equipment. The ASTM procedure says that Some articles have Google Maps embedded in them. After you rod each layer you need to tap the outside of your mold with an open hand about 10 to 15 times plastic molds may be damaged if you use a mallet to let excess air out of qstm cylinder and close the holes from rodding ASTM C31 Paragraph 9.
If representing pavements of a slab on grade, bank the sides and ends with earth or sand 31j must be kept damp, leaving the top surface exposed. The adtm diameter needs to be at least 3 times as wide as the largest piece of aggregate the nominal aggregate sizeso we only make 4x8s when the nominal aggregate size is less than 1. I would advise you to carry an extra set of each size of mold to every job, because you never know if you might be asked to make another set.
Once you’re back at the office, get the cylinders off of your truck and ashm of the transport racks, removing their bags.
Google provides ad serving technology and runs an ad network. Transportation time of cylinders shall not exceed 4 hours.
Step 2 If you are also doing slump, temperature, and air content on this sample, note that you must have these cylinders made within 15 minutes of receiving the sample, so plan accordingly and set up your work area beforehand ASTM C Paragraph 4. Cylinder molds can be metal or plastic, so long as they are non-absorbent, non-reactive to concrete, and maintain their shape and dimensions under all conditions asfm use.
These samples provide quality control for architects and engineers and allow them to determine if they will be able to put that concrete into service for their structure, or if they need to remove what they have poured. Use on a local area network or other network is not permitted.
ASTM C31 / C31M – 18b Standard Practice for Making and Curing Concrete Test Specimens in the Field
Transportation and Curing Procedures Cylinders need to be picked up anywhere from 18 to 48 hours after they are made. Some articles have Vimeo videos embedded in them. This is used to display charts and graphs on articles and the author center. When you are doing the last layer, if your mold is underfilled you can add extra concrete to keep it properly filled as you rod.
Link to Active This link will always route to the current Active version of the standard. Historical Version s – view previous versions of standard. They must not leak when water is poured into them empty. Rods – 6×12 cylinders need the large tamping rod and 4×8 cylinders need the small tamping rod. If the concrete design strength is 6, psi or greater, the initial curing temperature must range from 68 — 78 degrees F.
Warning; Fresh hydraulic cementitious mixtures are caustic and may cause chemical burns to exposed skin and tissue upon prolonged exposure. Cover each cylinder with an appropriate sized cylinder bag and place asttm in a protected location free of vibration and disturbances.
When planning to mold and cure concrete specimens, it is required that tests for slump, temperature, and air content be performed unless entrained air is not of concern to the project. While you are out there making cylinders you can keep lookout for errors in the mixing and pouring of the concrete; field techs are expected to report things that go wrong to the site superintendent or project manager.
ASTM C31 – Making and Curing Concrete Test Specimens in the Field
Typically for 6x12s we break 2 at the seven day mark and 2 at the 28 day mark and leave a spare cylinder to break on the 56 day mark if the cylinders have still failed to meet the required strength.
We may use conversion tracking pixels from advertising networks such as Google AdWords, Bing Ads, and Facebook in order to identify when an advertisement has successfully resulted in the desired action, such as signing up for the HubPages Service or publishing an article on the HubPages Service.
Work Item s – proposed revisions of this standard. You will get a representative sample of freshly mixed concrete from the truck or mixer, perform slump, temperature, and air content tests on it, and then make cylinders that will be taken back to the lab.
Excessive concrete buildup can be removed from metal scoops and rods by soaking them in vinegar overnight, aetm washing them off with soap and water and coating them with mineral oil to protect the galvanization. Be sure to write on your paperwork which location you are making or leaving your cylinders at, because someone else may be the one to come 3m them adtm.
Cylinders and beams can be placed in moist rooms or water storage tanks, but beams must be moved into water saturated with calcium hydroxide at the same temperature at least 20 hours prior to testing. If you are vibrating the cylinders to consolidate them, you will always have 2 equal layers to put into the mold, but for 4x8s you insert the vibrator one time per layer and for 6x12s you insert it twice per layer. Please choose which areas of our service you consent to our doing so.
For final curing, cylinders or beams must be placed in their curing storage no later than 30 minutes after removing from the molds. For a volume license the PDF is licensed to the person in which it is assigned.
Drive carefully, these are the only samples you’ve got. Wheelbarrow — Should be able to hold at least 1 cubic foot of concrete, the minimum size required for concrete strength testing specimens. Other product and company names shown may be trademarks of their respective owners. This supports the Maven widget and search functionality.
Ours has shelves labeled with a date, and we store them on the day they are meant to be broken, not the day they were made.