Installation instructions • Read online or download PDF • Rockwell Automation IF8 Compact IF8 Analog Input Module User Manual. Rockwell Automation IF8 Compact IF8 Analog Input Module User Manual – Download. Rockwell Automation IF8 Compact IF8 Analog. The Compact I/O modules can be used with a CompactLogix controller, IF4FXOF2F. IF8. IF16C. IF16V. IR6. IT6.
|Published (Last):||7 October 2004|
|PDF File Size:||15.48 Mb|
|ePub File Size:||2.14 Mb|
|Price:||Free* [*Free Regsitration Required]|
Mounting screws are required on every module. Your manual failed to upload The terminal screws are non-captive.
What’s missing? Tell us about it.
Host Controller Spacing for single-wide modules 35 mm 1. In that case, graphical screens are provided by the programmer to simplify configuration. Input Data File Word For each input module, slot x, words in the input data file contain the analog values of the inputs. Remove the label from the door, mark the identification of each terminal with permanent ink, and slide the label back into the door. The latches will momentarily open and lock into place. Locate holes every NC Wiring for channels are identical.
Overall hole spacing tolerance: The terminals will accept a 6.
Rockwell Automation IF8 Compact IF8 Analog Input Module User Manual | 32 pages
Your markings ID tag will be visible when the module door is closed. You can use the bare wire or a spade lug.
The same information applies to all channels.
Attach an end cap terminator 5 to the last module in the system by using the tongue-and-groove mankal as before. Approximate Shipping Weight with carton g 0. Wire fragments that fall into a module could cause damage at power up. For More Inform ation Replacing a Single Modu le within a System Channel 0 and 1 Configuration Data Channel 0 and 1 configuration data is shown below.
Route the wire under the terminal pressure plate. Lock the end cap bus terminator 6. Don’t see a manual you are looking for?
Ensure it is locked firmly in place. Rockwell Automation Support Rockwell Automation provides technical information on the web to assist you in using our products. Or point us to the URL where the manual is located.
However, some systems, 7169-if8 the ADN DeviceNet Adapter, also allow the bits to be altered as part of the control program, using communication rungs.
To allow communication between the controller and module, move the bus lever fully to the left 4 until it clicks. This lets you individually cancel each low process alarm latch. Tell us what’s missing.
Use a power supply that matches the input transmitter specifications. Loosen the terminal screws to be wired. Tell us about it. Use M4 or 8 panhead screws.